Please use this identifier to cite or link to this item:
WRRCSR No.12:28:84 Brackish Groundwater Desalting Tests Using Low Pressure Reverse Osmosis Membranes, Wai'anae, O'ahu, Hawai'i
|Title:||WRRCSR No.12:28:84 Brackish Groundwater Desalting Tests Using Low Pressure Reverse Osmosis Membranes, Wai'anae, O'ahu, Hawai'i|
|Authors:||Gee, Henry K.|
Lau, L. Stephen
|LC Subject Headings:||Brackish waters.|
Groundwater -- Hawaii -- Oahu.
Saline water conversion -- Reverse osmosis process.
|Date Issued:||Dec 1984|
|Publisher:||Water Resources Research Center, University of Hawaii at Manoa|
|Citation:||Gee HK, Lau LS. 1984. Brackish groundwater desalting tests using low pressure reverse osmosis membranes, Wai'anae, O'ahu, Hawai'i. Honolulu (HI): Water Resources Research Center, University of Hawaii at Manoa. WRRC special report, 12:28:84.|
|Series:||WRRC Special Reports|
|Abstract:||A desalting test using low pressure, reverse osmosis (RO) FT-30 and FT-50 membranes was conducted on Pump 10 well water at Oahu Sugar Company near Campbell Industrial Park on O'ahu. The brackish test water from the
Waianae basalt aquifer had a chloride (Cl-) concentration of 450 mg/l and a total dissolved solids (TDS) concentration of 1250 mg/l. The applied pressure ranged from 40 to 75 psi with a daily incrementof 5 psi. The
test operation duration was 239 hr. The FT-30 membrane demonstrated high rejection of Cl-, TDS, and silica (>90%), thus producing an excellent potable water. The permeate water production was slow, averaging 10.3 gpd or 4.6% of the feedwater. The production rate increased with pressure.
The fouling rate was slow and longer runs could be made before cleaning became necessary. The FT-50 membrane yielded high permeate production (approximately four times that of FT-30), but was of poor (sub-potable) water quality with average rejection of Cl- at 17% and TDS at 25%. The
fouling rate of the membrane was high, seriously reducing the permeate production in a short time. Cleaning with dilute phosphoric acid followed by Wisk and NaOH solution restored about 45% of the production rate. A large-scale RO module (element) should be tested for a longer period of time to determine sustainable performance of fouling rate. After reaching
15% reduction in the permeate production rate, various cleaning agents should be tested to restore the rate and to determine the type of fouling. By using a full-size commercial element, uncertainties of scale-up from small laboratory units can be eliminated. A longer operating period using
the available pump pressure would yield more meaningful design data than the short, 2-wk test period using laboratory-size elements.
|Pages/Duration:||iv + 21 pages|
|Appears in Collections:||
WRRC Special Reports|
Please email email@example.com if you need this content in ADA-compliant format.
Items in ScholarSpace are protected by copyright, with all rights reserved, unless otherwise indicated.