Please use this identifier to cite or link to this item:
WRRCSR No.9:19:86 Rotating Biological Contactor Pilot Study: Fort Kamehameha Wastewater Treatment Plant, Pearl Harbor, Hawaii
|Title:||WRRCSR No.9:19:86 Rotating Biological Contactor Pilot Study: Fort Kamehameha Wastewater Treatment Plant, Pearl Harbor, Hawaii|
|Authors:||Dugan, Gordon L.|
Takiguchi, Dean K.
biochemical oxygen demand
chemical oxygen demand
show 6 moreprimary wastewater treatment
rotating biological contactor
wastewater treatment efficiency
Fort Kamehameha WWTP
|LC Subject Headings:||Pearl Harbor (Hawaii)|
Sewage -- Purification -- Hawaii -- Oahu.
Sewage -- Purification -- Rotating disc process.
|Date Issued:||Sep 1986|
|Publisher:||Water Resources Research Center, University of Hawaii at Manoa|
|Citation:||Dugan GL, Takiguchi DK. 1986. Rotating biological contactor pilot study: Fort Kamehameha Wastewater Treatment Plant, Pearl Harbor, Hawaii. Honolulu (HI): Water Resources Research Center, University of Hawaii at Manoa. WRRC special report, 09:19:86.|
|Series:||WRRC Special Reports|
|Abstract:||A self-contained pilot unit (including primary and secondary sedimentation)
complete with electric motor driven plastic discs (surface area approximately 500 ft^2), located at the U.S. Navy's 7.5 mgd Fort Kamehameha Wastewater Treatment Plant (WWTP) at Pearl Harbor, Oahu, Hawaii, was operated from July 1985 to July 1986 at four different operating modes: hydraulic loadings of 1.5, 3.0, and 5.0 gpd/ft^2 (flat disc area) with discs exposed; and 5.0 gpd/ft^2 with discs covered. The influent for the RBC unit was primary clarifier effluent, which was very brackish for wastewater (4000-5000 mg/l chloride). In addition, wastewater from industrial-type
operations that use and discharge controlled/treated concentrations of
heavy metals were received at the WWTP. The median effluent BOD5 concentrations for the first two hydraulic loading rates (1.5 and 3.0 gpd/ft^2) were respectively 2.0 and 8.0 mg/l, with corresponding respective median
suspended solids values of 8.0 am 7.5 mg/l. These values were comparable with the present WWTP operation utilizing the activated sludge process. Hydraulic loadings at 5.0 gpd/ft^2 provided median effluent BOD5 concentrations in the 30 to 35 mg/l range. Heavy metal concentrations in the wastewater flows of the WWTP and RBC unit were considerably below the level of concern, while some accumulation of heavy metals was noted for the higher concentrations of suspended and settled solids--the mixed liquor suspended solids and the raw and digested sludge. Replacing the existing activated sludge component with an RBC component being hydraulically loaded at 3.0 gpd/ft^2 would require an estimated capital cost of approximately $2,500,000, which would require nearly 20 years to repay in electrical cost savings, based on a 10¢/kWh electrical cost, that increases in cost at an annual rate of 5%, and an interest rate of 8% compounded annually.
|Pages/Duration:||vi + 85 pages|
|Appears in Collections:||
WRRC Special Reports|
Please email email@example.com if you need this content in ADA-compliant format.
Items in ScholarSpace are protected by copyright, with all rights reserved, unless otherwise indicated.