ScholarSpace will be down for maintenance on Thursday (8/16) at 8am HST (6pm UTC)
Please use this identifier to cite or link to this item:
Modeling of virus transport in the subsurface, southern Oahu, Hawaii
|Title:||Modeling of virus transport in the subsurface, southern Oahu, Hawaii|
|LC Subject Headings:||Water—Pollution--Hawaii--Oahu.|
Viral pollution of water--Hawaii--Oahu.
|Issue Date:||Feb 1997|
|Publisher:||Water Resources Research Center, University of Hawaii at Manoa|
|Citation:||Orr S, Li J. 1997. Modeling of virus transport in the subsurface, southern Oahu, Hawaii. Honolulu (HI): Water Resources Research Center, University of Hawaii at Manoa. WRRC unedited report, 1997-01.|
|Series/Report no.:||WRRC Unedited Reports.|
Project Completion Report
|Abstract:||In this study, the potential is evaluated for viral contamination of groundwater in the southern Oahu aquifer, Hawaii, due to irrigation of sugarcane with effluent from secondary treatment plants. An EPA numerical model, CANVAS, has been modified and applied to simulate virus transport and its distribution in the subsurface of several sugarcane fields near the Pearl Harbor area. By incorporating the model with Monte Carlo simulations, the uncertainties and heterogeneity of the subsurface could be accounted for to some degree. The simulations show that due to natural disinfection provided by the geological and hydrological conditions in the testing fields, there is very low probability that viruses transported from irrigated fields by recharge water will reach drinking-water wells, although the virus concentration at the water table beneath the sugarcane fields is higher than a given criterion, 2 × 10-7 PFU/I. This is mainly due to the large backup distance between the wells and the virus sources, which allows viruses to die off before they reach the wells. The study suggests that a reasonably long setback distance is necessary for the areas where the thickness of soil is not large enough to allow all viruses to die off before they reach the water table or drinking water wells. In addition, care must be taken when the temperature in the subsurface is not high enough to assist the disinfection process|
|Sponsor:||Board of Water Supply: contract no. C33814|
|Pages/Duration:||vii + 107 pages|
|Appears in Collections:||WRRC Unedited Project Reports|
Please email firstname.lastname@example.org if you need this content in an ADA-compliant format.
Items in ScholarSpace are protected by copyright, with all rights reserved, unless otherwise indicated.